For increasing, move mouse over the picture
The leak indicating unit has 8 probe connections. By installing an expansion board, the number can be increased to 16.
Depending on the design of the probe suitable for monitoring shafts or double-walled pipes.
Collecting chambers, monitoring chambers and shafts
Liquids with a density higher than 0,7 g/cm3 that do not affect stainless steel.
The (possible) explosive vapor-air mixtures must be classifiable into gas group II A to IIC as well as in the temperature code T1 to T4.
Leak indicating unit: outside of Ex areas
Sensor (stainless steel float switch): zone 1
HOUSING / IP RATE:
Leak indicating unit: plastic box (pl-box) / IP 30
Leak indicating unit: -0 °C .. +40 °C
Sensor: -25 °C .. +60 °C
The requirements of the respective documentation must be observed!